The Smart Aquastat Control 32 can be configured via an iPhone or Android smart device. There are a variety of settings that can be modified but in general the controller should work fine with the default settings.
The Smart Aquastat Control 32 can be used simply as an on demand controller for your recirculation pump, or it can be configured to run on a timer via an iPhone or Android smart device so that it will keep the recirculation loop hot between specific times of day and on specific days of the week (up to 10 timers can be set). You can choose to use both on-demand and timers to customize the system to work best for you.
Even when a timer is active, the controller only runs the pump until the recirculation loop has heated up. Then, it shuts the pump off while continuing to monitor the recirculation loop temperature.
The app uses Bluetooth to communicate with the controller, so you must ensure Bluetooth is enabled on your smart device. The approximate range for Bluetooth reception is 30 feet from the controller. The Advanced Settings “Bluetooth Advertising Power” and “Bluetooth
Transmission Power” can be adjusted to provide a bit further range.
Do not “pair” the Bluetooth device; running the app will find and connect to the Smart Aquastat Control 32 and display the “Live Data”TM.
The blue LED on the controller will illuminate when the app is connected.
When the controller first boots it will be in provisioning mode. The green LED will first blink 3 times quickly and then blink steady on and off every second for 30 seconds. During this time the controller will advertise the default device name of “SmartCirc” and will not require a password to connect. Once connected the controller’s name can be changed via “Advanced Settings” to something unique and a password can be configured.
Once configured the app will remember the controller name and password and will connect to it automatically. If you install the app on a new device it will try and connect to the default name “SmartCirc”. If a device with that name is not found it will prompt you to select the device to which to connect and, if a password is set, prompt you for the password. To have this device remember the controller name you will need to go into “Settings→Advanced Settings→Controller Name” and press OK. It will be autofilled with the correct name.
To have the app always prompt you for the controller name, go into “Settings→Advanced Setting→Prompt For Device” and turn it on.
If you forget the password you will need to unplug the controller and plug it back in to enter provisioning mode so you can connect without a password.
The “Live Data”TM screen displays the temperature sensor value, the flow meter value, whether the pump is running, the current pump run time and if there is a timer active.
There is also a “Trigger Pump” button to activate the controller from the smartphone app.
This screen is useful for trouble shooting and configuration of the controller.
For example, if you find that the controller isn’t turning on when hot water is drawn from a faucet, this screen will show you the flow value the controller is seeing.
If the value is less than the Sensitivity setting, the controller will not turn on.
If the flow is greater than the Sensitivity setting and the controller doesn’t turn on then the temperature is greater than the high temperature value in the Temperature Range setting.
This screen provides for controlling all the settings of the firmware. There is a list of basic settings and the ability to expand the settings to show “Advanced Settings”.
The sensitivity setting allows the user to set how many flow meter pulses are required to turn on the controller. The default value is 20, which is fine for most installations.
If you find that the controller is not turning on when you turn a faucet on and off, you will need to decrease this value to make the controller more sensitive to flow (require fewer pulses to turn the controller on).
If you find that the controller is turning on when there is no timer active and no hot water being drawn, you will need to increase this number to make the unit less sensitive to fluctuations in flow (require more pulses to turn the controller on).
The temperature range setting allows the user to set the temperature values that cause the controller to turn the pump on and off.
When the controller senses flow or if a timer is active, it checks to see of the temperature sensor value is less than the low temperature value and if is, it turns on the pump.
It runs the pump until the temperature is greater than the high temperature.
You need to ensure that your water heater is set to a temperature greater than the high temperature setting or the pump will never turn off.
The default on temp (low temp) is 100°F, and the default off temp (high temp) is 105°F. These values work fine more most installations but can be modified to your own personal preference.
The maximum amount of time in minutes that that the pump will run when triggered regardless of temperature sensor values. This is a fail safe mechanism in the event a temp sensor comes loose from the pipe or the low temp difference isn’t met for some other reason. Default of 15 min.
This switch enables and disables the timers.
This can be used to turn the timers off when you go away on vacation or to simply turn them off if you just want to use the on-demand feature of the controller.
The Smart Aquastat Control 32 implements “Smart Timers”TM, which, regardless of this setting, will automatically disable if no hot water usage is detected within 24 hours.
The timers are re-enabled as soon as hot water flow is detected or the controller is connected to via the app.
Timers are disabled by default.
The dormant interval is the number of minutes that the controller lies dormant when the Max Pump Run Time is exceeded. The default value is 10 minutes.
The flow meter delay is the amount of time in hundredths of a second during which the controller counts the number of pulses that occur in the flow meter.
If the number of pulses counted is above the sensitivity threshold then the controller deems that there is flow in the hot water line.
The default value is 75 hundredths of a second which is fine for most installations.
This allows a name to be set on the controller that is something other than the default of “SmartCirc” so it can be distinguished from other controllers. This is useful if you have multiple controllers or if the installation is in a multi-tenant environment in a common utility room.
This allows you to set a password on the controller to prevent unauthorized access.
This causes the app to display a list of controllers to allow the selection of the device to which to connect. Setting this will automatically disable Connect Without Scan (Android only).
This is the power at which the Bluetooth radio advertises its presence. The app searches for this signal when connecting. The higher this value, the further away from the controller the app can find and connect to the controller. The default value is 5.
This is the power at which the Bluetooth radio communicates with the app once its presence is detected. The higher this value, the further away from the controller the app can be taken once the app is connected. The default value is 5.
With this setting enabled the app will scan for the controller the first time and then once connected will store the MAC address of the Bluetooth device to be able to more quickly connect in the future.
If the device is not online it will perform a full scan.
If you have more than one controller it is recommended to disable this feature and enable Prompt For Device.
This will reset the Smart Aquastat Control 32 back to the factory defaults. If the controller isn’t operating as expected, resetting to the factory defaults is a good thing to try to resolve the issue. You must type “yes” when prompted in order for the factory reset to take place.
This screen displays the timers. They are black when the timers are enabled and gray when then they are disabled via the “Timers Enable” setting. Tap the timer to edit or delete it. To add a new timer, tap the Add Timer button.
The Smart Aquastat Control 32 implements “Smart Timers,” which, regardless of the “Timers Enabled” setting, will automatically disable the timers if no hot water usage is detected within 24 hours. This is helpful if you go away on vacation and forget to manually disable the timers. They are re-enabled as soon as hot water flow is detected or the controller is connected to via the app.
The real time clock in the Smart Aquastat Control 32 is set when you connect to the controller with your smartphone. The Smart Aquastat Control 32 has a built in power backup that will keep the clock’s time for approximately 48 hours without power. After which the clock will lose its time and the controller’s timers won’t function until the time is set by running the app and connecting to the Smart Aquastat Control 32.
The clock does not adjust for daylight savings time so when the time changes you will need to connect to the Smart Aquastat Control 32 with your smart device and the time will be set to the time of your smart device.
Displays a rolling log of the last 256 controller activations.
The firmware of the Smart Aquastat Control 32 can be updated via the smartphone app. The app will notify you when you first connect if there is a new firmware available and selecting OK will navigate you to the Firmware screen.
By default only the firmware your type of controller will be displayed and if there is an update available it will be enabled. Tap on the firmware and then tap the “Update Firmware” button and the controller will begin the update process.
Do not allow the application to go to the background or the phone to sleep while the firmware update is running or the update will terminate. If the firmware is already installed it will be gray and not able to be selected.
The firmware release notes can be displayed by tapping on the question mark (?) or the firmware version number.
There is an option on this screen to “Show All Firmware Versions” which will display the firmware from our entire product line. The sensor requirements are different for the different firmware versions so updating to a different product without understanding the implications may provide unexpected results. Please see our web site for a description of the different products.