Smart Countdown Control 32
The Smart Countdown Control 32 can be used simply as an on-demand controller for your recirculation pump, or it can be configured to run on a timer via an iPhone or Android smart device so that it will keep the recirculation loop hot between specific times of day and on specific days of the week (up to 10 timers can be set). You can choose to use both on-demand and timers to customize the system to work best for you.
The app uses Bluetooth to communicate with the controller, so you must ensure Bluetooth is enabled on your smart device. The approximate range for Bluetooth reception is 30 feet from the controller.
The app can be downloaded for free from either Google Play or Apple App Store .
Do not “pair” the Bluetooth device; running the app will find and connect to the Smart Countdown Control 32 and display the “Live Data”TM.
The blue LED on the controller will illuminate when the app is connected.
(Initial screen displayed)
The “Live Flow”TM screen displays the flow meter value, whether the pump is running, the current pump run time and if there is a timer active.
There is also a “Trigger Pump” button to activate the controller from the smartphone app.
This screen is useful for trouble shooting and configuration of the controller.
For example, if the controller isn’t turning on when hot water is drawn from a faucet, the live data screen will show you the flow value the controller is detecting.
If the flow value is less than the Sensitivity setting, the controller will not turn on.
If the flow is greater than the Sensitivity setting and the controller doesn’t turn on, then the controller has run within the last dormant interval and won’t run again until the dormant interval has expired.
This screen provides for controlling all the settings of the firmware. There is a list of basic settings and the ability to expand the settings to show “Advanced Settings”.
The sensitivity setting allows the user to set how many flow meter pulses are required to turn on the controller. The default value is 20, which is fine for most installations.
If you find that the controller is not turning on when you turn a faucet on and off, you will need to decrease this value to make the controller more sensitive to flow (require fewer pulses to turn the controller on).
If you find that the controller is turning on when there is no timer active and no hot water being drawn, you will need to increase this number to make the unit less sensitive to fluctuations in flow (require more pulses to turn the controller on).
This setting allows you to set the amount of time the controller will run the pump when it is triggered. It is configurable up to 15 minutes with the default being 5 minutes.
This switch enables and disables the timers.
This can be used to turn the timers off when you go away on vacation or to simply turn them off if you just want to use the on-demand feature of the controller.
The Smart Countdown Control 32 implements “Smart Timers”TM which, regardless of this setting, will automatically disable themselves if no hot water usage is detected within 24 hours.
The timers are re-enabled as soon as hot water flow is detected, or the controller is connected to via the app.
Timers are disabled by default.
The dormant interval is the number of minutes that the controller lies dormant after sensing flow and heating up the loop.
As long as there is hot water flow within the dormant interval, the dormant interval timer is reset.
The dormant interval is also the number of minutes that the controller waits when a timer is active between pump runs. If you want the pump to turn on more quickly while a timer is active or more quickly between pump runs when you draw hot water, you will need to reduce this value.
The default value is 10 minutes which is fine for most installations.
The flow meter delay is the amount of time in hundredths of a second, during which the controller counts the number of pulses that occur in the flow meter.
If the number of pulses counted is above the sensitivity threshold, then the controller deems that there is flow in the hot water line.
The default value is 75 hundredths of a second, which is fine for most installations.
This setting allows high frequency pulses to be filtered out of the flow meter value to help prevent false triggers due to valves or fixtures in the plumbing opening or closing abruptly. Some examples are: solenoid valves for sprinkler systems, spray nozzles on hoses and toilet bowl fill valves.
The default value filters out pulses with a period of 19.0 ms or less. Before changing the default setting please read the Technical Details post.
This is the power at which the Bluetooth radio advertises its presence. The app searches for this signal when connecting. The higher this value, the further away from the controller the app can find and connect to the controller. The default value is 5.
This is the power at which the Bluetooth radio communicates with the app once its presence is detected. The higher this value, the further away from the controller the app can be taken once the app is connected. The default value is 5.
With this setting enabled the app will scan for the controller the first time and then once connected will store the MAC address of the Bluetooth device to be able to more quickly connect in the future.
If the device is not online it will perform a full scan.
If you have more than one controller it is recommended to disable this feature and the app will connect to the controller with the strongest signal (typically the closest controller).
This will reset the Smart Countdown Control 32 back to the factory defaults. If the controller isn’t operating as expected, resetting to the factory defaults is a good thing to try to resolve the issue. You must type “yes” when prompted in order for the factory reset to take place.
This screen displays the timers. They are black when the timers are enabled. If they are gray then they are disabled. Tap the timer to edit or delete it. To add a new timer tap the Add Timer button.
The real time clock in the Smart Countdown Control 32 is set when you connect to the controller with your smart phone. The Smart Countdown Control 32 has a built in power backup that will keep the clock’s time for approximately 48 hours without power. After which the clock will lose its time and the controller’s timers won’t function until the time is set by running the app and connecting to the Smart Countdown Control 32.
The clock does not adjust for daylight savings time so when the time changes you will need to connect to the Smart Countdown Control 32 with your smart device and the time will be set to the time of your smart device.
Displays a rolling log of the last 341 controller activations.
The firmware of the Smart Countdown Control 32 can be updated via the smart phone app. The app will notify when you first connect if there is a new firmware available and selecting OK will navigate you to the Firmware screen.
By default only the firmware your type of controller will be displayed and if there is an update available it will be enabled. Tap on the firmware and then tap the “Update Firmware” button and the controller will begin the update process.
Do not allow the application to go to the background or the phone to sleep while the firmware update is running or the update will terminate. If the firmware is already installed it will be gray and not able to be selected.
The firmware release notes can be displayed by tapping on the question mark (?) or the firmware version number.
There is an option on this screen to “Show All Firmware Versions” which will display the firmware from our entire product line. The sensor requirements are different for the different firmware versions so updating to a different product without understanding the implications may provide unexpected results. Please see our web site for a description of the different products.