Congratulations on purchasing the most advanced microprocessor-controlled, hot water recirculation pump controller made. This system is designed to run the recirculation pump only when you need it thus saving both water and energy. It is designed and built with pride in the USA to provide years of service and savings.
1 Smart Countdown Control 32 with RJ-45 connector
1 ¾” or 1” NPT Flow Sensor with JST connector
1 Wiring Harness with RJ-45 & JST connectors
Needed: The following items are needed for the installation, but are not included.
→ PTFE (Teflon) Tape
→ Wire fasteners for securing wiring to the wall
If this test fails, inspect the wires connecting to the flow meter to ensure they are not broken or loose. Reconnect the connection ensuring it snaps tightly and re-test.
If the pump fails to turn on see Trouble Shooting item 1.
GREEN LED: will blink 3 times when first plugged in to indicate the unit is functioning correctly.
GREEN LED: solid on when a timer is active and the pump is not running.
GREEN LED: will blink every 10 seconds when no other LED is lit (e.g. no timer active, pump not running)
RED LED: solid on when the pump is running whether due to a timer or due to demand.
BLUE LED: solid on when connected via the smartphone app.
Please read over the following instructions. If you are not comfortable with any part of them please contact a licensed plumber to perform the installation.
Prior to installation you must perform the system test at the beginning of the Quickstart Guide.
The Smart Countdown Control 32 can be used simply as an on-demand controller for your recirculation pump or it can be configured to run on a timer via an iPhone or Android smart device so that it will keep the recirculation loop hot between specific times of day and on specific days of the week (up to 10 timers can be set). Even when a timer is active it only runs the pump until the recirculation loop has heated up and then it shuts the pump off while continuing to monitor the recirculation loop temperature.
The app uses Bluetooth in order to communicate with the controller so you need to be sure that Bluetooth is enabled on your smart device. The app can be downloaded for free from either Google Play or Apple App Store . Do not “pair” the Bluetooth device, running the app will find and connect to the Smart Recirculation Control 32 and display the “Live Data”TM. The blue LED on the controller will illuminate when the app is connected.
This screen displays the flow meter value and whether the pump is running or there is a timer active. There is also a “Trigger Pump” button to activate the controller from the app. This screen is useful for troubleshooting and configuration of the controller. For example, if you find that the controller isn’t turning on when hot water is drawn from a faucet, if the flow value on this screen is less than the Sensitivity setting, the controller will not turn on. If the flow is greater than the Sensitivity setting and the controller doesn’t turn on then the controller has run within the last dormant interval and won’t run again until the dormant interval has expired.
This screen provides for controlling all the settings of the firmware. There is a list of basic settings and the ability to expand the settings to show “Advanced Settings”.
The sensitivity setting allows the user to set how many pulses of the flow meter are required to turn the controller on. The default value is 20 which is fine for most installations. If you find that the controller is not turning on when you turn a faucet on and off, you would decrease this value to make the controller more sensitive to flow (require fewer pulses to turn the controller on). Correspondingly, if you find that the controller is turning on when there is no timer active and no hot water being drawn, you would increase this number to make the unit less sensitive to fluctuations in flow (require more pulses to turn the controller on).
This setting allows you to set the amount of time the controller will run the pump when it is triggered. It is configurable up to 15 minutes with the default being 5 minutes.
This switch enables and disables the timers. This can be used to turn the timers off when you go away on vacation or to simply turn them off if you just want to use the on-demand feature of the controller. The smart Thermostatic Control 32 implements “Smart Timers” which, regardless of this setting, will automatically disable themselves if no hot water usage is detected within 24 hours. The timers are re-enabled as soon as hot water flow is detected.
Dormant Interval – The dormant interval is the number of minutes that the controller lies dormant after sensing flow and heating up the water line. As long as there is hot water flow within the dormant interval the dormant interval timer is reset. The dormant interval is also the number of minutes that the controller waits when a timer is active between pump runs. If you want the pump to turn on more quickly while a timer is active or more quickly between pump runs when you draw hot water you would reduce this value. The default value is 10 minutes which is fine for most installations.
Flow Meter Delay – The flow meter delay is the amount of time in hundredths of a second during which the controller counts the number of pulses that occur in the flow meter. If the number of pulses counted is above the sensitivity threshold then the controller deems that there is flow in the hot water line. The default value is 75 hundredths of a second which is fine for most installations.
Bluetooth Advertising Power – This is the power at which the Bluetooth radio advertises it’s presence. The app searches for this signal when connecting. The higher this value the further away from the controller the app can find and connect to the controller. The default value is 5.
Bluetooth Transmission Power – This is the power at which the Bluetooth radio communicates with the app once its presence is detected. The higher this value the further away from the controller the app can be taken once the app is connected. The default value is 5.
Reset to Factory – This will reset the Smart Recirculation Control 32 back to the factory defaults. If the controller isn’t operating as expected, resetting to the factory defaults is a good thing to try to resolve the issue. You must type “yes” when prompted in order for the factory reset to take place.
This screen displays the timers. They are black when the timers are enabled. If they are gray then they are disabled. Tap the timer to edit or delete it. To add a new timer tap the Add Timer button.
The real-time clock in the Smart Recirculation Control 32 is set when you connect to the controller with your smartphone. The Smart Recirculation Control 32 has a built-in power backup that will keep the clock’s time for approximately 48 hours without power. After which the clock will lose its time and the controller’s timers won’t function until the time is set by running the app and connecting to the Smart Recirculation Control 32.
The clock does not adjust for daylight savings time so when the time changes you will need to connect to the Smart Recirculation Control 32 with your smart device and the time will be set to the time of your smart device.
Displays a rolling log of the last 341 controller activations.
The firmware of the Smart Recirculation Control 32 can be updated via the smartphone app. The app will notify you when you first connect if there is a new firmware available and selecting OK will navigate you to the Firmware screen. By default only the firmware your type of controller will be displayed and if there is an update available it will be enabled. Tap on the firmware and then tap the “Update Firmware” button and the controller will begin the update process. Do not allow the application to go to the background or the phone to sleep while the firmware update is running. If the firmware is already installed it will be gray and not able to be selected.
There is an option on this screen to “Show All Firmware Versions” which will display the firmware from our entire product line. The sensor requirements are different for the different firmware versions so updating to a different product without understanding the implications may provide unexpected results. Please see our web site for a description of the different products.
ISSUE 1: If the controller has run within the dormant interval, the pump won’t automatically turn on when flow is detected.
RESOLUTION: Unplug the controller from power for 10 seconds and plug it back in. This will reset the controller and it will now turn on automatically when it detects flow. Turn a hot water faucet fully on for 1 second and then turn it off. If it still doesn’t turn on see ISSUE 2.
ISSUE 2: The sensitivity value is set too high for the controller to detect the flow provided by your faucet.
RESOLUTION: Open the smartphone app to the “Live Flow” view. This will show what flow value the controller is sensing. Turn the hot water faucet fully on and watch the flow value. If it goes greater than 20 then the pump will turn on. If it doesn’t go greater than 20 then you will need to reduce the sensitivity value to be less than the maximum value you observed. NOTE: If you are seeing very low flow at the faucet it is possible the aerator in the faucet is clogged. Removing it and tapping it to remove any accumulated sediment can restore the flow, but they are inexpensive so replacing it is recommended.
ISSUE: Pressure spikes in the cold water supply line caused by abrupt turning on or off of the cold water (for instance when a toilet fills or a sprinkler system turns on or by fluctuations in the feed from the utility company) can cause the Smart Recirculation Control 32 to trigger the hot water recirculation pump to turn on.
RESOLUTION: The sensitivity value of the Smart Thermostatic Control 32 is too low and should be adjusted higher. The default value of 20 works well, but can be susceptible to these false triggers. It is recommended to increase it by 5 pulses at a time to filter out these anomalies.
ISSUE 1: A wire connecting the flow meter is broken.
RESOLUTION: Inspect the wiring harness where it connects to the flow meter to ensure none of the three wires appear broken. If they are contact Leridian Dynamics to get a replacement harness. If it looks good see ISSUE 2.
ISSUE 2: Sediment or scale is blocking the flow meter.
RESOLUTION: To ensure that this is indeed the issue perform the following test. Remove the sensor from the flow meter that is held on with 2 small silver screws (don’t worry, it won’t leak water when the sensor is removed). Start the smartphone app, view the “Live Flow” screen, and quickly wave a magnet back and forth over the sensor. You should see the flow value change. The flow meter works by spinning a magnet on a turbine that is read by the sensor. If you see a flow value in the smartphone app then the flow meter is blocked with sediment or scale and will need to be removed and cleaned. If you do not see a flow value then there is an issue with the sensor and/or the wiring harness and it will have to be replaced.